August 25, 2014 by kaeserusa
By: Michael Camber
If you’ve got a compressed air system, then you’ve got condensate. Hopefully, you also have condensate drains on aftercoolers, filters, dryers, tanks, and air lines throughout your system. Condensate drains are often overlooked but serve a vital function. Condensate is mostly water, but it also contains oil, dirt, and other materials. If you aren’t properly draining it from your system, you can contaminate your products and cause wear and downtime in your production equipment.
There are three basic categories of drains:
- “Demand” drains automatically activate to remove condensate but only if it is present.
- “Timed” drains automatically activate based on timers, whether condensate is present or not.
- Manual drains are simply valves that rely on someone to open and close them.
Although not as popular as they once were, timed electric drains are still relatively common. They have been around for years and are comparatively low in price. These drains have two timers, an interval and duration timer and automatically open based on these settings. When they open, compressed air is vented and pushes out the condensate. They are simple and most people think of them as a “set it and forget it” solution, but they will vent costly compressed air whether condensate is present or not. The timers can be adjusted seasonally to minimize wasted air…but we’ve never seen it done.
Also, timed drains blast high pressure air into the condensate (AKA oil-water) separator. Depending on the fluid type, this can create emulsions which inhibit oil/water separation. Further, the high pressure air may damage some types of condensate separators.
Another solution is the automatic demand drain, which only activates when condensate is present, saving valuable compressed air. Some cost a bit more than timed electric drains, but the annual savings they provide by not wasting compressed air, makes up for the extra cost. They also improve condensate separator function which lowers disposal costs.
Don’t believe that these drains can really make much difference on your utility bill? Consider this. During a compressed air audit walk-through for a steel mill with a 5,672 cfm system, the auditors calculated the mill was losing $11,320 every year by using timed electric drains:
So take a walk around your plant and see what kind of drains you have on your filters and tanks. Switching to demand drains could give you some quick and easy savings while improving the effectiveness of condensate disposal.
Michael Camber is currently Kaeser’s Marketing Services Manager. He has been in a number of sales, marketing and training roles since joining Kaeser in 1997. Michael has been a member of Kaeser’s active training team, educating both Kaeser’s distribution network and customers on reliable and energy efficient compressed air system design